Upon inspection found service cable casing deteriorating and starting to allow water into the panel which was oxidizing the aluminum neutral. Replaced the old 200 amp service as per proposal. Installed new 200 amp service cables. Sleeved the service cable to protect cable and prevent water infiltration. Replaced old panel with new square DQO panel and breakers with free whole house surge protection. Updated all grounding to code. Pulled all necessary permits and will coordinate all inspections and BGE hook up to the new wiring.